Identify deficiencies that may impact IEQ and/or sources of odor concerns. Typically includes the following depending on the nature of concern, but not limited to:
- interview/questionnaire of concern individual(s)
- inspection above drop ceiling (condition of roof deck, pipe insulation, return air plenum)
- inspection of ventilation system (operation of variable air volume box and outdoor air dampers, check controls, measurements of carbon dioxide, temperature and relative humidity, sources near outdoor air intake, measure return and supply air volume, cleanliness of coils, liner and condensate pan)
- inspection of exterior
- inspection below drop ceiling (housekeeping, sink and floor drain traps, signs of past and present moisture concern via visual and/or moisture meter, mold growth, ensure connection of current and capping of abandoned sanitary vents, odorizers, excessive plants and fabric items, identify potential pathways, and measure volatile organic compounds, carbon monoxide, and lighting)
The flag had been removed prior to the Office of the Environment's assessment.
The remainder of the room was assessed. Minor relative humidity mold growth (just starting) was observed underneath of some of the chairs in the room.
Building Services (HVAC) assessed the unit ventilator serving the room and found that the set-points were set incorrectly.
The mold growth observed on the bottom of chairs was cleaned/disinfected upon discovery. Custodial Services was instructed to clean all surfaces within the room as a precaution.
Building Services (HVAC) adjusted the temperature set-points.